H-A-S Static Phase Converter
Used with a Reversing Drum Controller
If controller used has overload protection, select heater coils from the tables shown on Page 5. The top two contacts shown above should have their heater coils selected on T3 amperage, and the bottom contact heater coil should be selected based on L2 amperage. If the controller being used differs from the controller pictured, the proper terminals should be chosen that perform the contact sequences shown.CAUTION: The circuit breaker or safety switch should be open before disconnecting any wiring.
Used with a Reversing Magnetic Starter Controller
When using common control (or control power from CPT), be sure to use control power from L1 and L2. (L2 must be brought from load side of disconnect switch.)
Size OL1 per L1 column from table on Page 5. Size OL2 and OL3 per T3 column from table on Page 5.